text:
musingsheader image
Helpful? 0

Saving Energy With Manual J and Manual D

Experts tell builders that HVAC equipment and ducts should be designed according to Manual J and Manual D; the problem is, no one wants to do the calculations

Posted on Aug 13 2010 by Martin Holladay, GBA Advisor

If you’ve been paying attention to energy-efficiency experts and green-building Web sites, you probably know that it’s important to properly size your HVAC(Heating, ventilation, and air conditioning). Collectively, the mechanical systems that heat, ventilate, and cool a building. equipment. Most sources repeat the same advice: oversized furnaces and air conditioners cost too much, waste energy, and sometimes provide lower levels of comfort.

To avoid these problems, the first step is to insist that your HVAC contractor perform a Manual J calculation to determine the heat loss and heat gainIncrease in the amount of heat in a space, including heat transferred from outside (in the form of solar radiation) and heat generated within by people, lights, mechanical systems, and other sources. See heat loss. for each room of your house under peak (worst-case) conditions. Then your contractor can specify equipment that meets Manual J requirements.

If you’re building a new home, your contractor should design your duct system using Manual D. (Manual D depends on the room-by-room heat loss and heat gain numbers supplied by the Manual J calculations.)

Sounds easy, right? Well, it isn’t. In most areas of the country, it’s very difficult to find a residential HVAC contractor who is willing to perform Manual J and Manual D calculations.

Helpful advice from your government
According to the U.S. Department of Energy’s Office of Energy Efficiency and Renewable Energy, “Homeowners should insist that contractors use a correct sizing calculation before signing a contract. This service is often offered at little or no cost to homeowners by … conscientious heating and air conditioning contractors.” Yeah, right.

The government Web site goes on to advise, “When the contractors are finished, get a copy of their calculations, assumptions, and the computer printout or finished worksheet.” Well, that’s easy for you to say. But just see how easy it is to get that paperwork from Bob once his Do-It-Right HVAC Service has finished installing your new air conditioner.

Easy enough for an 8th grader to do it — Quick, find me an 8th grader
Manual J and Manual D are calculation worksheets published by the Air Conditioning Contractors of America (ACCA). For many years, these worksheets have been the standard methods for calculating residential heat loss, heat gain, and duct sizes.

Manual J and Manual D calculations are no longer performed with a pencil and paper; contractors now use software programs. Hank Rutkowski, the mechanical engineer who wrote (and continues to update) Manual J, explained to me how Manual J calculations are performed: “To bridge the gap between the complexity of the paper manual and the contractor you have to have software. It was never our intention that people do the calculations by hand. The manual serves as a guide to computer programmers. The key is the software, which takes the complexity and makes it simple enough for an eighth grader to use. … The contractor never has to deal with the equations.”

The best-known Manual J software programs are Elite RHVAC, Wrightsoft Right-J8, Adtek AccuLoads, and EnergyGauge.

Software programs for Manual D duct design include Elite DuctSize and Wrightsoft Right-D.

A Manual J heat loss and heat gain calculation considers most of the factors that affect HVAC equipment sizing, including the climate; the size, shape and orientation of the house; the home's air leakage rate; the amount of insulation installed; the window areas, window orientations, and glazingWhen referring to windows or doors, the transparent or translucent layer that transmits light. High-performance glazing may include multiple layers of glass or plastic, low-e coatings, and low-conductivity gas fill. specifications; the type of lighting and major home appliances; and the number and even the age of the occupants. For the calculations to be meaningful, information on all of these factors must be correctly entered into the software program.

Manual J and Manual D calculations are required by most building codes
The 2006 International Residential Code requires (in section M1401.2) that “Heating and cooling equipment shall be sized based on building loads calculated in accordance with ACCA Manual J or other approved heating and cooling calculation methodologies.”

Furthermore, IRCInternational Residential Code. The one- and two-family dwelling model building code copyrighted by the International Code Council. The IRC is meant to be a stand-alone code compatible with the three national building codes—the Building Officials and Code Administrators (BOCA) National code, the Southern Building Code Congress International (SBCCI) code and the International Conference of Building Officials (ICBO) code. section M1601.1 requires that “Duct systems serving heating, cooling and ventilation equipment shall be fabricated in accordance with the provisions of this section and ACCA Manual D or other approved methods.”

There's some wiggle room in the code, of course; individual inspectors can theoretically approve “heating and cooling calculation methodologies” other than Manual J. But the intent of the code is to outlaw rule-of-thumb sizing — for example, “one ton of cooling per 400 square feet.”

Where can I find a contractor to do it?
As with many code provisions, the requirement for Manual J and Manual D calculations is widely ignored and rarely enforced.

Most residential furnaces, boilers, and air conditioners are still sized by rules of thumb instead of careful calculations. As a result, almost all of the HVAC equipment installed in U.S. homes is oversized. Dozens of studies have confirmed that the degree of oversizing typically ranges from 30% to 200%.

Builders and homeowners who ask HVAC contractors about Manual J and Manual D calculations are usually met by a blank stare. One homeowner posting under the name Tom21769 posted the following anecdote on the HVAC-Talk Web forum: “I’ve had a bunch of contractors out, most of them sales reps but a couple with technical/repair backgrounds, and not a single one has brought up the subject of Manual J. In one case, when I asked about getting one, the guy did not know what I was talking about. They all seem to assume that if a 2-ton system is in here now, that's what the replacement needs to be.”

On his GBA blog, Carl Seville recently reported, that it “is difficult to obtain … an accurate HVAC Manual J calculation. It seems that few HVAC contractors understand how to prepare an accurate report, often oversizing systems out of habit rather than designing them for the actual house loads. Also, while the reports are supposed to be delivered before the equipment is installed, they rarely are, and mistakes are usually identified well past the time to make any corrections.”

Another GBA blogger, Michael Chandler, reported, “When I have asked my HVAC contractor what it would cost to add Manual D, he responds that a $12,000 system with J alone would be $15,000 with D. That may be his way of saying that he doesn’t know how to do it, but the fact remains that this is a very common situation with residential HVAC contractors who can barely implement Manual J.”

Elsewhere, Michael Chandler wrote that his local planning board was “still not even enforcing the Manual J requirement which results in inefficient, oversized air conditioners and attendant humidity and mold problems. Even though reps of the local HBA pointed out the benefit of requiring Manual J, the county is still not requiring proof that a Manual J has been done to award a certificate of occupancy.”

On another GBA page, energy consultant Allison Bailes wrote, “HVAC contractors, at least here in the Southeast, don’t often do Manual J load calculations at all. They mostly use rules of thumb based on square footage (e.g., 500 square feet per ton of AC capacity). When they take the time to enter data and run a Manual J, they usually do it incorrectly.”

Even when they do the calculations, the results are usually wrong
In his posted comment, Bailes raised an interesting point: the problem of “garbage in, garbage out” (GIGO) Manual J calculations. Several energy experts have commented on the GIGO problem, including John Proctor, Hank Rutkowski, and Allison Bailes.

Hank Rutkowski, the mechanical engineer who wrote the original Manual J document, was recently interviewed for a profile posted on the Green Building Talk Web site. The piece notes, “Rutkowski estimates that only 10% of heating and cooling equipment sizing decisions are based on some type of Manual J calculation and that less than 1% of the jobs are based on an aggressive implementation of the recommended design procedures.”

Rutkowski explains the GIGO problem this way: “Manual J is a good tool if you use it aggressively. Follow the rules and it will give you a reasonable margin of safety. But the average contractor says, ‘Better safe than sorry,’ so he fudges here and there. He adds 5 to 10 degrees to the summer and winter design temperatures, calls the building ‘average’ instead of ‘tight’ and doesn't take credit for shading by interior blinds and drapes. Then when he finally comes up with a load number for sizing, he throws in an extra half-ton of AC just for the heck of it.”

For a high-performance home, sizing by Manual J may still result in oversizing
Several years ago, I had a conversation with building scientist Joe Lstiburek about air conditioners installed in Building America homes in Las Vegas. “HVAC designers are committed to the institutional oversizing of air conditioning equipment,” Lstiburek told me. “The average system is sized at 150% to 200% of the requirements of Manual J. They oversize because they don’t know what they will get for a building envelopeExterior components of a house that provide protection from colder (and warmer) outdoor temperatures and precipitation; includes the house foundation, framed exterior walls, roof or ceiling, and insulation, and air sealing materials., and to compensate for duct leakage and inappropriate refrigerant charge. If you size according to Manual J, there is already a fudge factor built in. But most designers then add another fudge factor.”

According to Lstiburek, their experience proved the high-performance Building America homes in Las Vegas could have had HVAC systems sized at about 60% of Manual J. To be conservative, his team recommended installing systems sized at 80% of Manual J.

Does oversizing matter?
There are strong arguments against routine oversizing of HVAC equipment. The best argument is simple: oversized equipment usually costs more than right-sized equipment.

Oversized equipment suffers from short cycling. For example, an oversized furnace brings a home up to temperature quickly, and then shuts off. A few minutes later, it comes on again, only to shut off quickly. Many homeowners find the see-saw sound of a short-cycling furnace to be annoying.

When air conditioners short cycle, the units don't run long enough to achieve much dehumidification — at least in theory. (During the first few minutes of operation, an air conditioner cools a house. But not enough moisture has collected on the cold coil or on the pan below for any water to have actually gone down the drain. When the air conditioner turns off, all of the moisture in the pan and on the coil just re-evaporates.)

The conventional wisdom may be wrong, however
Increasing evidence shows that energy experts have exaggerated the negative effects of equipment oversizing, however. Studies have confirmed that oversized furnaces don't use any more energy than right-sized furnaces. Moreover, newer modulating or two-speed furnaces operate efficiently under part-load conditions, solving any possible problems from furnace oversizing.

Although there are ample reasons to believe that oversized air conditioners are less effective than right-sized equipment at dehumidification, at least one field study was unable to measure any performance improvements or energy savings after replacing an existing oversized air conditioner with a new right-sized unit.

The bottom line
The main reason to choose right-sized equipment is to avoid paying too much money for equipment you don't need. A Manual J calculation will ensure you don't spend more than necessary for your furnace, boiler, or air conditioner.

Moreover, a Manual J calculation will provide room-by-room heat loss and heat-gain information that is essential to good duct design. Without good duct design, you're running the risk of comfort complaints.

Last week’s blog: “Sealing Ducts: What’s Better, Tape or Mastic?”

Image Credits:

  1. Florida Solar Energy Study
Fri, 08/13/2010 - 07:33

Florida "Studies"
by John Brooks

Helpful? 1

I don't see how you can draw any conclusions from testing air conditioners in typical poorly built Florida Homes that have air handlers in garages and attics,Low R-value walls AND ceilings that resemble Swiss Cheese.
I think as we improve our enclosures that Right Sizing will have much more benefit than just saving money on equipment.

Fri, 08/13/2010 - 08:10

J first, then S, T, D
by Allison A. Bailes III, PhD

Helpful? 0

Great article, as always, Martin. Of course, there's always more you could've written, but you have to keep your articles from turning into books, so let me raise a few more points that didn't make the cut above.

First, Manuals J & D don't stand alone. Once you get the loads (Manual J), you have to select equipment (Manual S) and work out some of the air distribution issues (Manual T) before designing the duct system (Manual D). To do all this correctly, you have to understand air flow - static pressure, friction rates, net free area... As you pointed out, most HVAC contractors don't even understand J, much less S, T, or D.

Second, one problem you didn't mention in regards to short cycling is the decreased equipment life. It's starting up and shutting down that causes most of the wear and tear, so short cycling equipment probably doesn't last as long. I haven't seen a study of that, though, so let me know if you're aware of one.

Third, I learned from you over in the Q&A section here at GBA a while back about another FSEC study showing that right-sized cooling systems can sometimes make the relative humidity higher in a house. Of course, that comes from looking at only one part of the system - the equipment size - without considering the effect of the ducts.

Now, let me give you an example of right-sizing gone wrong. This was a spray foam insulated house with equipment put in according to Manual J loads, but the contractor didn't do anything different about the duct design than he usually does. The cooling systems couldn't keep up in summer, however, with temperatures barely getting below 80 F with the units running continuously. I measured the air flow with a flow hood, and the 7 tons of equipment capacity was moving 5 tons worth of air - 2000 cfm instead of 2800 cfm.

As with everything else in this field, you have to take a systems view and not focus on one detail.

Fri, 08/13/2010 - 09:10

Response to John
by Martin Holladay, GBA Advisor

Helpful? 0

You wrote, "I don't see how you can draw any conclusions" from the cited FSEC study.

In response, let me say that I draw exactly the conclusion that the Florida data support: replacing an existing oversized air conditioner with a new right-sized unit probably won't save energy or improve occupant comfort, unless duct location, duct leakage, and duct insulation problems are simultaneously addressed.

We all owe a debt of gratitude to researchers. Their data are essential to the advancement of building science. Don't throw the baby out with the bathwater. Read the study and find out what it means.

Fri, 08/13/2010 - 09:40

I do Respect and admire FSEC
by John Brooks

Helpful? -1

Sorry about my new construction "tunnel vision"
I will read the study more carefully.
I did not realize that this article and "The bottom line" was strictly about replacing Existing equipment.

Fri, 08/13/2010 - 11:32

HVAC Sizing
by Armando Cobo

Helpful? 0

I so agree with Dr. Bailes on ALL 4 MANUALS. It’s amazing to me how most HVAC contractor don’t even know what you are talking about when you ask for all 4 manuals. Adding more to the problem is that most manual Js are run with the wrong design temperature, wrong multiplier, and etc. etc.

Fri, 08/13/2010 - 15:38

Response to Allison
by Robert Latvala

Helpful? -1

The scenario you layout is exactly what I am seeing with my HVAC contractor. He runs manual S and J but that is as far as he will go. The attitude I get is that duct work will deliver the right amount of air no matter how it is run.

I have recently been trying to put all of my duct work in conditioned areas. We build on crawl spaces so on a 2 story home the 1st floor ducts come up from a sealed crawl and on the 2nd floor ducts go between holes in floor trusses.

We are seeing issues on the 2nd floor with comfort. It feels humid even with the A/C running for long periods of time. We are using a 1.5 ton 14 SEER heat pump for about 1340 SF. The Manual J says the cooling load is about .8 tons. A 1.5 ton unit is the smallest available according to my contractor.

I would suspect that I am losing air flow because of the way duct work is run through the trusses. Bends and branches in flex duct work without a plan. If the unit was truly oversized I wouldn't think humidity would be an issue. I also need to consider that the Manual J has incorrect inputs in it.

The home tested at 3 ACH and I received a HERS rating of 60. I am using batt insulation, house wrap, and caulking or filling around holes and cracks that penetrate the thermal envelope.

Do you need some certfication to run these manual calculations? I am at a point where I would like to do my own for the piece mind that my contractors are the same. In the end it will be my problem if the unit doesn't operate correctly.

Fri, 08/13/2010 - 15:57

Response to Robert Latvala
by Martin Holladay, GBA Advisor

Helpful? -1

1. Manual J and Manual D calculations are required by code.

2. These calculations are necessary because they provide you with design airflows in CFM for each room.

3. Every HVAC system needs to be commissioned. Commissioning includes measuring the airflow at the coil, and the airflow at each register in every room, to verify that the delivered cfm matches the design cfm.

4. If your HVAC contractor skipped some of these steps, there's no way of knowing what's wrong with your system.

5. If your HVAC contractor can't step up to the plate, you'll have to hire a home performance contractor, an energy consultant, or an engineer to perform the necessary design work, verification testing, and equipment commissioning.

Fri, 08/13/2010 - 16:18

Wisconsin study too
by Michael Blasnik

Helpful? -1

You might be interested in a fairly recent study by the Energy Center of Wisconsin where they swapped out an air conditioner for one of a different size and found no difference in energy use. it was part of a report summarizing A/C research work there that had lots of other interesting stuff. You can download it from their web site A direct link is

There is very little data to suggest significant energy savings from 'right-sizing" equipment. Smaller equipment has some cost advantage but perhaps it's biggest benefit is that the previously undersized duct system is not as undersized when you install smaller equipment. Of all the ACCA manual's, I'd be most concerned with following D for comfort and probably energy efficiency. .

I'd be interested in any data people can find showing an impact on equipment lifespan, because I've heard that claim before but never seen any data to support it.

Fri, 08/13/2010 - 21:53

Robert Latvala
by Gene Wilhoit

Helpful? 1

I have to chime in to note the system approach to these problems. A system that consists of a good air barrier, thermal barrier, and all HVAC inside the building envelope is the only way to acheive proper conditions for the manuel calculations to be totaly true. With proper ventilation this would be the perfect building.
First, the contractors do not have a clue about air barriers, they do not believe the attic should be sealed and fiberglass batt insulation is the greatest thing since sliced bread.
There is not a HVAC contractor in the country that can overcome all of these faults of the builder.
In their defense, in the coastal southeast humidity you cannot expect a 55 degree coil in a 140 degree attic to not condensate profusely. The HVAC contractor knows that in these building conditions, if he follows manuel J he will get calls in the summer for too hot and calls in the winter for being too cold. The easy thing for him to do is oversize so he does not get these phone calls. That is how it happens every day.
If a "system" is followed everybody contributes to the success of the "system" instead of trying to blame one subcontractor (HVAC) for everybody elses shortcomings. United we build a workable system, divided we build pretty much as is common today.

Oh yeah, Robert I was going to mention your exposed crawlspace as a major humidity source. An encapsulated floor and duct system, or an encapsulated crawl space would act the same as a vapor barrier under a concrete slab. They all control the evaporation effect (humidity) from entering under a building
Putting all HVAC equipment and ductwork in conditioned space not only extends the service life of the equipment, but the maintenance and energy savings are nothing to sneeze at. Speaking of sneezing, an HVAC system inside the building envelope with a good air and thermal barrier and properly ventilated will leave you nothing to sneeze at.

Fri, 08/13/2010 - 22:13

Who should be responsible for calculating heat load
by Andrew Henry

Helpful? 0

I can understand that one would expect an HVAC contractor do a manual J calculation when retrofitting a furnace/air conditioner. But I don't think they should be the one determining heat load for new construction.

Shouldn't it be a requirement that new homes/buildings be designed with the heat load in mind right from the start? Kind of like Passive House! An artifact of the architect/designer/builder's design is the heat load. God forbid we still think it is acceptable that a designer be able to go through the design process for a building without knowing what the heat load is when they come out the other end of an iterative design process?

Designers/architects probably still aren't using pen and paper to design buildings.
If the designer can design the building using software they ought also to be able to resolve the buildings heat load as well.

It seems everyone is letting off the designer of the building a little to easily.

Fri, 08/13/2010 - 22:35

Andrew re:designers/architects
by Hunter Dendy

Helpful? 0

Andrew, I'm glad to hear someone say that. I'm an architect and have recently been certified a HERS rater and now working on learning the HVAC 'manuals' software. I agree with the house-as-a-system design approach and intend on going forward with that methodology....and not leaving anything up to subcontractors that I might have no control over the selection of.
As always, great discussion guys.

Sat, 08/14/2010 - 10:19

Equipment sizing
by Doug McEvers

Helpful? 0

While the 2 stage funaces cover a wide range of heating loads, AC sizing is more important. A properly sized cooling unit will run longer between cycles and take out more indoor humidity than an oversized one. The cooling setpoint can be higher as the lower indoor humidity level will feel comfortable.

Sat, 08/14/2010 - 10:52

I third this sentiment
by j chesnut

Helpful? 0

Heating systems design, both the determination of the heat load and the design of the distribution system, are best done as the thermal envelope and the room layout of the house are being designed. As Hunter said some architects/designers are already taking on this responsibility and I have seen schematic approach integrated into some architecture courses at universities.

When we design custom homes at our office we use CAD software that creates a virtual 3D model. It is very convenient to pull the necessary quantities required for the calculations. Also different systems can be overlayed (structural, electrical, mechanical, etc) to visualize for conflicts and efficiencies.

My understanding is that Manual J, Manual D and the HERS system are based on ASHRAE heat load calculations. ASHRAE heat load calcs are simplified to not account for solar or internal heat gains (although I think ASHRAE cooling calcs do).

What is the best software tool for American designers? I don't think HERS is rigorous enough. The
Passivhaus PHPP is German import and I am unable to understand it 100% because it references German standards that are not translated into English. I don't know if PHIUS (the US Passivhaus institute) has the capacity to provide the support necessary to have the PHPP be consistently used in the American market. The PHPP works very well when you can use European components (windows, ventilation equipment) that have been certified by the Passivhaus Institute. Its a little bit of approximation when domestic equipment is used.

We need a fully developed and supported American PHPP. What institute will head this? The grassroots PHIUS that is an embassy for PHI? I think this should fall on ASHRAE's lap but this becomes a turf war between the architects and HVAC contractors.

Sat, 08/14/2010 - 11:09

Manuals & HVAC Design
by Armando Cobo

Helpful? 1

In almost all jobs I design we get a Mechanical Engineer involved to do all manuals and design the HVAC the right way. As a rule I never let the HVAC contractor do that work. An ME is an independent, third party designer who is not biased to oversize the system and with his designs my clients get much better bids.
I can count in one hand the HVAC contractors capable/willing to do the correct calculations and design in 12+ years of designing high performing homes.

Sat, 08/14/2010 - 13:21

Armado, Do you employ ME's on
by Hunter Dendy

Helpful? -1

Armado, Do you employ ME's on residential projects or just commercial? I've found it difficult to bring another engineer's fees into the mix on residential. I think that would be the way to go if my clients would agree.
I agree with J chestnut that we need much better energy/envelope modeling software. Remrate is fine, but it doesn't take into account enough about the actual geometry of the house. I would like to see more rigorous solar studies on the model to determine heat gains.

Sat, 08/14/2010 - 20:25

ME & Manuals
by Armando Cobo

Helpful? 0

I do use a ME on all residential projects. You may have to shop around; when we first started, prices where pretty high ($1.00/sf +), but they came down in the last 10 years or so. Now that the market is bad, prices have come down even more. Now it’s around $0.50 per sf in NM. In TX I did found an HVAC contractor to use his ME but it took four calculations and redesigns and a “come to Jesus” meeting for them to agree to do it correctly. I do review all work before the Builder/Customer makes the final decision.
Supply and Demand will work on lower prices. It is my experience that I get much smaller equipment, better duct design (4 manuals), higher quality installation inspected by the ME and a final commissioning and balancing of the system.
In climates where humidification and dehumidification is highly needed, you should run Manual P. If you use Heat pumps, Manual H. If you use Hydronic, Manual GAMA H22. If you are zoning, Manual RS.

Sun, 08/15/2010 - 19:43

Straw man?
by James Morgan

Helpful? 1

Here in central NC we've been beating the drum on right-sized mechanicals for decades now and I've never once heard the claim that the intent of the right-sizing approach was energy savings. The Florida study could not be more irrelevant to the true issue here which is maintaining indoor air quality through proper dehumidification and reducing opportunities for condensation and mold growth within the conditioned envelope. This study was conducted on homes with terminally compromised thermal/hygric enclosures. As a cautionary tale of why you shouldn't expect miraculous results from poorly conceived piecemeal upgrades it has some value but I'd hate to see it quoted as a reason NOT to apply best-practice engineering to mechanical systems in properly built homes.

Mon, 08/16/2010 - 07:32

Another complication - heat pumps
by John Semmelhack

Helpful? 2

In heat pump territory (such as here in Virginia), "right-sizing" heat pumps might be leading to an overall increase in energy use. Heat pump systems are sized to the cooling load. If the design heat load is greater than the capacity of the heat pump at design temperatures, then an electric resistance heater kit is added to the system to make up the difference. I'm seeing a lot of cases where "right-sized" heat pumps are quite a bit undersized for the heating load, thereby leading to an increase in the use of the inefficient electric resistance heater.

Behold the recent case of an Energy Star house I rated where the heat pump was "right-sized" to match the cooling load, but at design heating conditions, was only able to satisfy about 25% of the load. The other 75% of the load was handled by electric resistance heating. This is not a good way to save energy.

Mon, 08/16/2010 - 10:11

Size of AC
by Doug McEvers

Helpful? 0

The picture of the smaller compressor unit where the original one stood says little. The most efficient AC units these days have a large cooling fin surface and the appliance is really big compared to older, less efficient models.

Mon, 08/16/2010 - 20:42

Verifying Manual J
by RichK

Helpful? -1

I believe there are many reasons contractors don’t provide quality Manual J’s. I have herd so estimate that 80% of the residential HVAC change out market is not permitted. If true it’s not hard to figure out why many don’t do them. Poorly done Manual J’s usually stem from a lack of training and/or review. Educated homeowners and contractors should insist they get a copy of the manual j before they give any deposits. I recommend you review some of the basics it’s not very hard or time consuming. I have included links to ACCA’s site that should help anyone trying to review the manuals for accuracy.

Manual J Verification (For Inspectors)

Manual D Verification (For Inspectors)

Manual S Verification (For Inspectors)

Understanding and Using the HVAC Design Review Form

Illustrated Example One

Illustrated Example Two

Some basic issues I see every day that are incorrectly reported on Manual J’s; design temperatures, area and volume, duct system location, insulation values, window areas, orientation, ventilation systems, infiltration rates. Most of these are easy to spot with a quick review. The only way we can expect the industry to get better is by raising the bar. If you don’t insist on getting a proper Manual J you probably won’t.

The contractor that wants to charge thousands more to do a Manual D makes me chuckle. If the contractor has invested in software to do the calculations its nothing more then a few mouse clicks. It just proves he is ignorant about the technology.

Rich K

Thu, 08/19/2010 - 14:13

Passive House
by Greg Duncan

Helpful? 0

j, Hunter:

I agree that architects should be more involved in calculating heat and cooling loads as part of a systematic design process. The Passive House Planning Package (PHPP) allows architects to do this with some training. I don't think it's necessary to have a separate American version. There is some tweaking that could make it easier for us in the US. For example, allowing direct input of NFRC data for windows.

The US Department of Energy evaluates building energy modeling software and has this to say about PHPP:

PHPP calculates energy demand for buildings. It is compatible with international norms (ISO 13790) and well validated with dynamic simulation tools as well as with measured data. It is especially adapted to high-performance buildings and can be used to prove Passive House requirements. The planning package comprises many tools specifically useful for the design of high-performance buildings.

The Passive House Planning (Design) Package (PHPP) includes:

energy calculations (incl. R or U-values)
design of window specifications
design of the indoor air quality ventilation system
sizing of the heating load
sizing of the cooling load
forecasting for summer comfort
sizing of the heating and domestic hot water (DHW) systems
calculations of auxiliary electricity, primary energy requirements:
(circulation pumps, etc.), as well as projection of CO2 emissions
verifying calculation proofs of KfW and EnEV (Europe)
Climate Data Sheet: Climate regions may be selected from over 200 locations in
Europe and North America. User-defined data can also be used.
lot of tools useful in the design of passive houses, e.g. a calculation
tool to determine internal heat loads, data tables for primary energy factors
a comprehensive handbook, not only introducing PHPP use, but also
highlights crucial topics to be considered in Passive House design.

energy design and thermal comfort for high performance buildings, esp. passive houses

Multizonal dynamic building simulation for buildings with large glazing areas (solar gains) and/or high need of control

Sat, 08/21/2010 - 17:11

Missing the forest for the trees, or the ducts for the equipment
by Dan Perunko

Helpful? -2

I always feel like the growing body of research that shows oversizing to be unimportant is oversimplified. In your next blog you comment on the energy saving available by using a smaller blower, do we leave that out when discussing condensing unit sizing? Also are we discussing correctly installed systems vs correctly installed systems? If so then the oversized system will require significantly larger ducts, which are much more difficult to run well through a truss system or a chase. It seems to me that right sizing is significantly easier and more effective. My company is a small home performance company in california and we are undersizing manual J on all our jobs. Our average system works out to be about 1000 square feet per ton, we are able to guarnetee even comfort and low opperating cost. All of this is possible in part because the smaller equipment allows us to build duct systems that we can fit into the houses. What would you rather install a 12" duct or a 20" duct?

Sat, 08/21/2010 - 22:27

Agree with Dan Perunko
by John Brooks

Helpful? 1

Extremely Good Enclosures
Smaller systems with smaller ducts
That's how we can get the HVAC Monster out of the attic.
LOW-CAL or Passivhaus or Passivhaus-like

I do not agree with the prevailing Florida strategy or that "R-10 walls are probably plenty" in the South.

Sun, 08/22/2010 - 04:08

Response to Dan Perunko
by Martin Holladay, GBA Advisor

Helpful? -1

Dan Perunko,
In case there is any uncertainty about my position:

1. I believe strongly in the importance of proper Manual J and D calculations, and I believe strongly in the importance of right-sizing rather than oversizing. There are multiple benefits that accrue from doing it right.

2. I caution builders not to overpromise. We should be wary of promising energy savings due to right sizing. Nevertheless, right sizing is clearly the way to go.

Mon, 08/23/2010 - 05:03

sizing is important for furnaces, too
by David Butler

Helpful? 1

That depends. Unless the furnace and duct system are located inside the envelope, the heat absorbed by the mass of the system will be lost to unconditioned space every time the system cycles off. Due to higher temperature differential, this is a bigger issue for furnaces than for air conditioners and heat pumps.

As you point out in the blog, oversized equipment can also lead to comfort issues. This is especially true for furnaces In high performance homes, where gross oversizing is not uncommon. If a furnace only runs 20 minutes out of the hour on a design day, perimeter zones will experience significant temperature droop before the thermostat "sees" the load (the longer the off cycle, the more pronounced the droop). Under part-load conditions, a furnace's minimum run-time logic causes the opposite problem - overshoot.

In warmer climates, heat pumps are ideal for high performance homes because they operate continuously at high loads and are unlikely to cause overshoot at part loads. The key is to design the shell so that supplemental heat is minimized. In homes with poor insulation, non-existent air barrier and leaky ducts in the attic, a heat pump may not be the best choice.

But at a significant price premium. A properly sized single-stage furnace will not overshoot at part load. BTW, if the smallest available furnace that can carry the cooling load is more than 150% of the design load, then a gas-fired hydronic coil may be the best option, assuming natural gas is available.

You make all the right arguments and then drop this bomb? Notwithstanding your Aug 22 comment, this conclusion steals the thunder from your article.

In full disclosure, I earn my living providing 3rd-party HVAC design services for high performance homes. For a qualitative, yet exhaustive look at oversizing, see my 2009 RESNET presentation on HVAC for high performance homes:

David Butler

Mon, 08/23/2010 - 05:48

Response to David Butler
by Martin Holladay, GBA Advisor

Helpful? 0

1. I stand by my statement that "Studies have confirmed that oversized furnaces don't use any more energy than right-sized furnaces." If you can cite a study that shows significant energy savings attributable to replacing an existing oversized furnace with a new right-sized furnace, I'd love to read it.

2. Your hypothetical savings are predicated on cases where the furnace and duct system are located outside the thermal envelope. Of course, substantial savings accrue from moving a furnace and ductwork from an unconditioned attic or garage to within a home's conditioned space. The GBA Web site has consistently emphasized the importance of this fact. (To those of us who live in the Northeast or the upper Midwest, it's always astonishing to imagine that anyone would by nutty enough to put a furnace in an unconditioned attic.) But don't attribute these obvious available energy savings to right-sizing; these savings are due to obeying the important principle of locating the HVAC equipment and ductwork where they belong.

3. I agree that a single-stage furnace is often the best option, and that the upgrade to a two-stage furnace doesn't always pencil out (in terms of energy savings).

4. You quote my article -- "The main reason to choose right-sized equipment is to avoid paying too much money for equipment you don't need" -- and then append a comment: "You make all the right arguments and then drop this bomb?" It's not a bomb; it's true. I'm a strong believer in energy conservation, but I also believe that it's important for energy consultants to base their advice on data. Cite studies if you have them.

Sat, 09/11/2010 - 10:37

HVAC contractor got defensive
by Michael Schonlau

Helpful? -2

I met with an HVAC contractor and my builder the other day. When I brought up my requirement to have Manual J and a Manual D calculations done prior to me making a final decision on any equipment, the HVAC rep literally told me I could "wipe my a!@ with a Manual J" and that it didn't provide any useful real world info. Instead, the two HVAC reps asked me for the square footage of my home and threw out "that will probably need 3-1/2 ton equipment". They didn't even know anything about my wall/roof construction, R-values, windows, or overall approach to energy conservation. The meeting was very disappointing.

Mon, 09/13/2010 - 10:27

Response to Michael Schonlau
by Martin Holladay, GBA Advisor

Helpful? -1

Your story is one more example in the growing pile of anecdotes that shed light on this issue. Even though Manual J calculations have been code-required for years, the word has not apparently gotten out to HVAC contractors yet ...

Register for a free account and join the conversation

Get a free account and join the conversation!
Become a GBA PRO!


Content-Type: application/http; msgtype=response

WARC-Type: response

text:
Road Maintenance on Your Dirt Road

Hollis Walker shares low-tech solutions for road maintenance on your dirt road to help keep your driveway and roads in good shape.
By Hollis Walker
September/October 2006

This swampy lagoon of a road demonstrates the most common problem in maintaining rural roads — drainage.

Content Tools

Learn about these low-tech solutions for road maintenance on your dirt road.

Most of the time, living on a country road feels almost like heaven, as John Denver sang. But when your darling dirt road turns to mud soup after a rain or your ditches overflow into your fields, living on a country road can feel more like being stuck in purgatory.

If it’s a public road you live on, you may be literally stuck — at least until the government road grader bails you out. But if you own the road or share ownership of a road with your neighbors and feel you’re forever struggling to keep it passable, take heart: There are solutions for road maintenance on your dirt road.

In some parts of the country, road improvement is no longer optional. Wildfires that scorched the West have emphasized the need for better road access for firefighting equipment; new ordinances are mandating wider roads with better turnarounds. Environmental studies show that much freshwater pollution and soil erosion is caused by unchecked runoff from dirt roads, prompting calls for improved road construction and drainage on private as well as public byways.

You may be thinking, "Right. But I can’t afford to fix the road."

That might not be the case, according to Richard Casale, district conservationist for the U.S. Department of Agriculture’s Natural Resource Conservation Service, based in Capitola, California.

"There are some things that can be done to significantly improve a road and increase its longevity without having to cost an enormous amount of money," Casale says. A believer in low-tech solutions for the average homesteader, Casale also explains that installing expensive structures like culverts can create new problems.

"It gives you a false sense of security when you put a structure in," he says. "Every structure requires maintenance."

How to best deal with your road depends on its original construction, soil, climate, traffic and other factors. But all roads share some common traits.

Russ Lanoie, of Conway, New Hampshire, whose business includes dirt and gravel road construction and maintenance, says problems with dirt and gravel roads can be boiled down to three principles: "Drainage. Drainage. Drainage." Whether you have ruts, potholes, gullies, roadside erosion, cave-ins or ditches that look like lakes, the root of the problem is usually the road’s inability to handle water.

The key to good drainage is to cooperate with nature, not to battle it, according to Kevin Abbey, director of the Center for Dirt and Gravel Road Studies at Pennsylvania State University. Try to discover the natural drainage patterns of the landscape around your road and accommodate the water flow.

The most important thing to encourage proper drainage on roads located on gentle terrain is to make sure that the road has a "crown" — that it is higher at the center than at its sides — so water will drain to ditches or off onto the surrounding landscape, and not stay on the road. A crown should be 1/2 to 3/4 of an inch high for every foot of the road’s width from centerline to side, according to Lanoie. For example, a road that is 20 feet wide (10 feet from crown to either side) should have a crown 5 to 7 1/2 inches higher than the edge of the road.

A tractor or truck with a blade can be used to create or reshape a crown. Surface materials should be redistributed evenly afterward.

Instead of a crown, some roads will drain better if they’re graded to slope all to one side. Woody Colbert, former member of the Pennsylvania Conservation Commission, says a road could be side-sloped when the slope of adjacent land is moderate and water flow can be maintained over the road and into that land. Sharply curved roads often are good candidates for sloping inward, which also forces traffic to slow. Such roads require an inside ditch.

Banking a road outward is trickier, since the far edge from which water is draining will have a tendency to erode. Almost every country dweller has seen a crack in the roadside enlarge over time until a bank gives way. On suitable sites, however, out-sloped roads are generally cheaper to install, less expensive to maintain and have fewer erosion and drainage issues.

The primary outlet of drainage is usually the roadside ditch. But not all ditches are created (or maintained) equally. To handle the most water, a ditch should have a parabolic or flat bottom, not a "V" shape. Strong vegetation or a rock lining will help prevent erosion. (Tip: Use rocks the size of those left behind by storm water.) A ditch that’s constructed and operating effectively should be carrying fairly clear water that never gets closer than a foot from the roadside.

Culverts — metal, plastic or concrete pipes installed under roadbeds to channel runoff — are not always the best solution for drainage, but they are common and sometimes necessary. Unless you have heavy equipment and some expertise at road building, you’ll probably need to hire someone to install a culvert.

"Always oversize culverts," Casale says. Sedimentation can reduce water-carrying capacity significantly, and debris can block culverts, so bigger is always better. The water will find its way beyond a culvert, and if the pipe is too small or blocked, excess flow will destroy the culvert and might wash out the roadbed.

On the downstream side of culverts, it’s important to provide some means of energy dissipation — something that will break up the force of the water, such as some large rocks — or the water you’ve channeled can destroy the roadside ditch and/or the surrounding landscape. Anything that slows the water down without blocking it entirely will help.

To prevent storm debris from blocking the upstream side of a culvert, create a debris barrier — but not at the mouth of the pipe, Casale says. If a barrier is too close to the culvert mouth, it can promote damming of debris. Instead, walk upstream from the culvert 5 or 6 feet. Drive lengths of steel pipes or fence posts into the ditch base at regular intervals across its width, the aim being to block large pieces of debris. For a 24-inch culvert, place the barriers 12 to 15 inches apart; for a 36-inch culvert, install 18 to 24 inches apart at approximately the depth of the ditch; and so on.

The best low-tech solution to cross-drainage — directing water from one side of the road to another — are what Casale calls "rolling dips." These are wide but shallow depressions constructed across a road’s width, which naturally channel water off the road. Rolling dips should be dug 3 to 6 inches deep at an angle of 45 to 60 degrees from the centerline of the road. Lanoie recommends replacing the removed dirt or material with crushed angular stone, then adding road surfacing gravel mix atop that.

If your road is in very bad shape, you may be forced to consider rebuilding it, at least in part. Even if you hire someone to do the work, make sure they’re following advice from experts.

The base of a road should be constructed of coarse gravel with "fines" (clay and silt particles), so it drains well. Roads should be surfaced with crushed stone that is angular, so the sharp edges of the rocks compact into each other like pieces of a puzzle, helping to create a solid top layer. (Don’t use round rocks; they roll out of the roadbed.) Lanoie recommends a maximum stone size of 1 inch in diameter.

Surfacing material also needs fines to hold it together. Often aggregates typical of what you might purchase at a gravel quarry, sometimes called "base course," are combinations of stone and fines that are ideal for building paved roads, but not so great for surfacing gravel roads.

Tests by the Center for Dirt and Gravel Road Studies have shown that a higher percentage of fines will provide a much tighter-packed gravel road and perform better than typical aggregate. A "recipe" for the center’s recommended aggregate mix is available on its website, www.dirtandgravelroads.org. (Look under "Resources" for "Driving Surface Aggregate Specifications.") When ordering gravel from the quarry, ask for more fines. Sometimes such mixes are referred to as "dirty."

These fines are also key to problems with dusty roads. Too few fines and the aggregate doesn’t bind together, allowing the tiny particles to be kicked off the surface by fast-moving traffic. Too many fines and the same results occur, plus some very slick mud. Solving perennial problems with dusty roads may take some experimenting with the addition of surface fines.

Another solution is spreading calcium chloride powder on the road. Calcium chloride absorbs moisture from the air and thus binds the surface materials together. While calcium chloride is a definite environmental improvement over the old practice of spreading used motor oil on dirt roads, it can adversely affect the environment and in some places may be illegal to use on roads. Check with your state’s environmental department. Calcium chloride doesn’t work in arid climates.

Maintaining dirt and gravel roads isn’t easy. Still, experts say, a good gravel road is less expensive and easier to maintain than a paved one. But like everything else on a country property, roads benefit most from close attention and quick action when something goes wrong.

"In the old days, in a bad rainstorm, the farmer went out with a hoe and cut herringbones off the side of the road, so the water would go off the side instead of washing out the middle of the road," Lanoie says. Judicious use of a shovel when trouble starts and thoughtful follow-up for permanent solutions can make living on a country road glorious once again.

Previous | 1 | 2 | 3 | 4 | Next

Post a new comment

10/21/2013 1:03:44 PM

10/21/2013 1:02:37 PM
one of the worst offences is filling pot holes with gravel alone, especially round gravel. water collects around the gravel and lubricates it so that traffic immediately pounds it out. Fill hole partially with gravel then a layer of dirt to fill the spaces between the rock then put a layer of gravel on top the traffic will pound into the dirt. This will usually shed water and prevent the reappearance of the pot hole.

Pay Now & Save 50% Off the Cover Price

First Name: *
Last Name: *
Address: *
City: *
State/Province: *
Zip/Postal Code:*
(* indicates a required item)
Canadian Subscribers - Click Here
Non US and Canadian Subscribers - Click Here

Live The Good Life with Grit!

warcinfo:
robots: classic
hostname: ip-10-183-142-35.ec2.internal
software: Nutch 1.6 (CC)/CC WarcExport 1.0
isPartOf: CC-MAIN-2014-10
operator: CommonCrawl Admin
description: Wide crawl of the web with URLs provided by Blekko for March 2014
publisher: CommonCrawl
format: WARC File Format 1.0
conformsTo: http://bibnum.bnf.fr/WARC/WARC_ISO_28500_version1_latestdraft.pdf


text:
213 W A St Kannapolis, NC 28081

Virginia’s supplies female shoppers with an array of high-quality threads from Pendleton, Windridge, and other popular lines to meet the demands of special events and day-to-day sartorial situations. Maxi dresses ($68+) offer shoulder-to-ankle aesthetic adornment, and knit sundresses ($68+) stylishly protect skin from the sun's smoldering rays. Visitors can browse a selection of Fashque knit tops ($49+) and Caribe print tanks ($38+), as well as Rochelle three-quarter-sleeve cotton tops ($34+), which adorn torsos and help wearers master basic fractions. Virginia’s personable, passionate staff assists patrons with everything from choosing a mother-of-the-bride dress to fashioning the ideal outfit for an underwater scavenger hunt.

Nearby Places


text:
Eight Laser Hair-Restoration Treatments or One Intensive Hair-Loss Treatment at Elite Emage (Up to 80% Off)

Value Discount You Save
$500 80% $401
Give as a Gift
Over 20 bought
Limited quantity available

Hair follicles often become emaciated due to constantly expending energy to retain their vise-like grip on the scalp. Bulk up thinned-out strands with this Groupon.

Choose Between Two Options

Elite Emage

Elite Emage's technicians employ diverse hair replacement and restoration techniques to keep clients' scalps blanketed in luxuriant hair. Custom-built wigs fill in sparse spots left from alopecia, chemotherapy, and jump-starting a hot air balloon burner. Extensions of many varieties add glamorous length to natural locks. Low-level-laser treatments and topical solutions try to stop existing strands from jumping ship to other people's heads at the same time that they promote the growth of new follicles. Stylists proffer salon services, such as cuts, coloring, and up-dos, to keep heads properly preened and coiffed.

In a Nutshell

30-minute laser treatments aim to restore hair's fullness; 90-minute intensive treatment stimulates scalp to address hair loss and damage

The Fine Print

Experiences that can impart a more youthful appearance


text:
SVAT Digital Wireless DVR Security System Bundles (Up to 35% Off). Two Options Available. Free Shipping and Returns.

Online Deal

Value Discount You Save
$199.99 35% $70
Over 40 bought
Limited quantity available

The Deal

SVAT digital wireless DVR security systems with SD card recording and long-range night vision cameras. Choose from the following options

  • $129.99 for a system with a 7" LCD monitor and one camera ($199.99 list price)
  • $199.99 for a system with a 7" LCD monitor and two cameras ($299.99 list price)

SVAT Digital Wireless DVR Security Systems

Even in the dark, SVAT's security cameras can pierce the shadows to see up to 40 feet away. That means the system watches over your home all day and all night, with 2GB SD cards recording up to 350 minutes of video. The systems come with a 7" LCD monitor that makes it easy to watch what's going on, but the receivers can also connect to TVs via an included AV cable. The bundles all include four window warning stickers, which let potential miscreants or serial loiterers know they're being watched.

  • Sets up in seconds
  • Clear digital video
  • Three recording modes: manual, scheduled, and motion-activated
  • Systems support up to four cameras
  • Includes 2GB SD card; compatible with SD cards up to 32GB
  • Records up to 350 minutes of video on 2GB SD card
  • Long-range night vision cameras
  • 40-feet viewing range in the dark
  • AV cable connects to most televisions made after 1776
  • One-year warranty from manufacturer
  • Click here to view a complete contents list for each option.

In a Nutshell

Long-range night vision cameras peers through up to 40 feet of darkness, recording video to receiver or LCD monitor

The Fine Print

Do it yourself, from home repairs to renovation projects


text:
Zen Double-Hose Hookah. Multiple Colors Available. Free Shipping.

Online Deal

Value Discount You Save
$64.95 46% $29.96
Over 630 bought
Limited quantity available

Hookah Contents

  • Double-hose hookah
  • Two matching colored hoses with grommets
  • Matching colored stem
  • Matching colored base
  • Matching colored clay bowl with grommet
  • Pair of hookah tongs with hole puncher

Zen Double-Hose Hookah

Double-hose hookah is great for small parties and other friendly gatherings by letting two people smoke at a time.

  • Colorful matching hookah set
  • Two hoses for better social element
  • All pieces necessary for setup
  • Handsome design can serve as centerpiece
  • Multiple colors available

In a Nutshell

Full hookah set entertains guests and friends with a colorful design and two hoses so multiple people can smoke at once

The Fine Print

Expires Dec 14th, 2013. Limit 3 per person, may buy 2 more as gifts. Limit 1 per order. Free shipping. Does not ship to AK/HI/Canada/Puerto Rico. Most orders ship within 2 1/2 weeks from the redemption date. Does not ship to PO boxes. FINAL SALE; no returns unless defective. See return policy. Must be 18+ to order and redeem. Voucher is non-transferable. See the rules that apply to all deals.

Everything you need to entertain in style


text:
Events & Activities in Waterbury

Event & Activity Deals

Up to 56% Off Personal Career Assessments

$125 $59

108 picture cards uncover clients' personality traits and obstacles, with job-specific cards helping to open up a new career path

Up to 51% Off Safety and CPR Courses

667 Main Street

$50 $25

Women's safety course covers awareness of potential threats, protection of themselves and their families, and performing defensive skills

63% Off Cardio Kickboxing Classes

$40 $15

Burn calories and de-stress during one-hour kickboxing classes that teach self-defense, discipline, and centeredness

Up to 69% Off Women’s Yoga Classes

$150 $49

Up to 47% Off at Pequabuck Golf Club

$120 $59

$12 for a Ghost Tour

Multiple Locations

$25 $12

Up to 51% Off Tutoring or Test-Prep Course

$180 $89

One-hour tutoring sessions for kids from preschool through 12th grade cover any subject; SAT class includes covered materials

Up to 81% Off Kickboxing Classes

$100 $29

Kickboxing challenges students to punch and kick through energized sessions; Krav Maga teaches street-effective self-defense techniques

Up to 52% Off at Westwoods Golf Course

$87.28 $43

Up to 76% Off Ballroom-Dance Lessons

$95 $29

Up to 50% Off Painting Class from Paint Craze

On Location

$35 $17.50

Passionate artists teach you how to paint specifically for a canvas during fun, social events with drinks

50% Off

New Britain

$40 $20

Up to 67% Off Boot Camp

$99 $39

Up to 50% Off at Indoor Water Park

$38 $21

55% Off from Oxford Flight Training

$265 $119

The flight-instruction package includes pilot handbooks, a logbook, and an hour of flight

Up to 74% Off Kickboxing Packages

On Location

$105 $30

Up to 76% Off at CrossFit Gulls

$125 $49

Up to 53% Off Archery Lessons

$60 $29

Six-hour certification courses qualify graduates to teach others the art of basic archery for a three-year period

Multiple Locations

$140 $19

Up to 74% Off Women's Kickboxing Classes

$149.95 $39

44% Off Personal Training

$70 $39

Up to 56% Off a BYOB Painting Class

$25 $12

Adults bring their favorite beverage to the painting class, which allows them to unwind while creating a masterpiece

Half Off Yoga or Pilates Classes

$120 $59.99

Yoga and Pilates classes help burgeoning students to explore exercise, breathing, and meditation in order to create stronger bodies

50% Toward one Month of Unlimited Yoga

$100 $50

Up to 44% Off Guided Painting Night

Multiple Locations

$45 $25

Under the guidance of an experienced artist, guests reproduce copies of the night's painting while sipping drinks and listening to tunes

25% Off Membership to Edgewood Bath and Tennis Club

$1,836 $1,385

Families gain access to state-of-the art swim, tennis, and fitness facilities, with water-spray features and a playground for the kids

94% Off MetaBody Yoga & Fitness Pass

Multiple Locations

$350 $20

Up to 52% Fitness Model Show

Toyota Presents Oakdale Theater

$183.95 $89

Fitness models compete in categories such as Male Fitness Model and Diva Bikini Model to earn pro status

50% Off Wine-Blending Class

$80 $40

76% Off Fitness Packages at Horizon Personal Training

$190 $45

HIIT classes use short intervals that can help with rapid fat loss and increased cardiovascular capacity and endurance.

Up to 54% Off Horseback-Riding Lessons for Two

$100 $49

Up to 59% Off Martial-Arts Classes

$95 $39

62% Off at CrossFit Southington

$154 $59

Up to 55% Off Dance Classes

$50 $25

Up to 88% Off Group Fitness Training Classes

Farmington Professional Park

$599 $89

Up to 54% Off Fitness Classes at The Posture Bar

$105 $49

Up to 88% Off Karate Classes

Unionville / Farmington

$239.99 $29

Select Local Merchants

56 Lexington St
New Britain,

95 South Turnpike Road

230 John Karbonic Way
New Britain,

Winding Trails works to preserve natural woodlands and waterways around the Farmington area, hosting recreational activities that foster a love of the outdoors. In addition to renting out ski equipment to visitors eager to ski over scenic forest trails, the group runs outdoor adventure programs, day camps for ages 3-13, and swim lessons.

50 Winding Trl

If you add up the doctors of chiropractic, licensed massage therapists, and registered yoga teachers, Balanced Body Chiropractic Center has more than 15 wellness professionals working to help clients heal and strengthen their bodies. The Center specializes in chiropractic—the practice of making small adjustments to fix misalignments of the spin—aiming to treat maladies such as allergies, joint dysfunction, neck and back pain, and headaches. In addition to adjustments, the Center’s professionals offer healing and relaxing massage therapy, yoga, acupuncture, hypnotherapy, and psychotherapy.

223 Meadow St

300 Welch Rd


text:
Chicken Slow Cooker Recipes

67 recipes to browse.
Filtered by
  • bell peppers
  • slow-cook
Narrow your search
Use the filters in this column to find the perfect recipe.
Ingredient Filters
meats vegetables fruits dairy hot & spicy uncategorized seasonings & flavorings

Maybe List

When you're ready, we'll help you decide between similar recipes.

Holding 0 recipes


text:
Chocolate Covered Matzah Recipes

86 recipes to browse.
Narrow your search
Use the filters in this column to find the perfect recipe.
Cuisine Filters
Ingredient Filters
vegetables fruits dairy chocolate nuts uncategorized seasonings & flavorings
Cook Time Filters

Maybe List

When you're ready, we'll help you decide between similar recipes.

Holding 0 recipes


text:
Ham Roll Up Recipes

41 recipes to browse.
Filtered by
  • Under 5 minutes
Narrow your search
Use the filters in this column to find the perfect recipe.
Ingredient Filters
meats vegetables fruits cheeses dairy uncategorized seasonings & flavorings

Maybe List

When you're ready, we'll help you decide between similar recipes.

Holding 0 recipes


text:
Southwest Salad Dressing Recipes

99 recipes to browse.
Filtered by
  • sugar
  • vinegar
Narrow your search
Use the filters in this column to find the perfect recipe.
Ingredient Filters
meats vegetables fruits dairy hot & spicy uncategorized seasonings & flavorings
Cook Time Filters

Maybe List

When you're ready, we'll help you decide between similar recipes.

Holding 0 recipes


text:
Three Cheese Dip Recipes

23 recipes to browse.
Filtered by
  • eggs
Narrow your search
Use the filters in this column to find the perfect recipe.
Cuisine Filters
Ingredient Filters
meats vegetables cheeses dairy hot & spicy uncategorized seasonings & flavorings
Cook Method Filters
Cook Time Filters

Maybe List

When you're ready, we'll help you decide between similar recipes.

Holding 0 recipes


text:
Velvetta Potato Soup Recipes

23 recipes to browse.
Filtered by
  • vegetable broth
Narrow your search
Use the filters in this column to find the perfect recipe.
Ingredient Filters
meats vegetables fruits dairy hot & spicy uncategorized seasonings & flavorings
Cook Method Filters
Cook Time Filters

Maybe List

When you're ready, we'll help you decide between similar recipes.

Holding 0 recipes


WARC-Truncated: length

text:
Santa Cruz Community Calendar
Community Calendar Print EMAIL help
Prospective Tutor Orientation
From Wednesday, January 09, 2013 -  06:00pm
To Monday, January 21, 2013 - 07:00pm
Find out how you can change someone's life. Become a volunteer tutor with the Literacy Program of Santa Cruz County. No foreign language or teaching experience required. Does require patience and a one-year commitment of two hours per week. Free training provided.
Location : 1740 17th Avenue, Santa Cruz
Contact : Genie Dee


text:
Santa Cruz Good Times

Mar 15th
Text size
  • Increase font size
  • Default font size
  • Decrease font size

In Defense of Education

news1_protestParticipants in the March 4 UCSC protests share their stories
“I am a language teacher!” UC Santa Cruz Italian lecturer Giulia Centineo screamed into the loudspeaker during a March 4 protest at UC Santa Cruz. Centineo held the microphone up to her lips and addressed the crowd, her hand trembling, perhaps out of nervousness or simply passion. “For years the administration has been shoving down our throats the idea that students are clients. No, students are students! I don't sell Italian! I teach Italian!”

An army of fists shot up in the air and cries of solidarity rang out across the intersection of Bay and High streets, which had been blocked off by protestors since early that morning.

Hundreds of UCSC students, faculty and supporters attended the protest at the base of campus as part of a state and system-wide Day of Action to Defend Public Education. Students came to protest the spike in student fees, which have increased 300 percent since 2002 and will increase another 15 percent this upcoming fall quarter. Professors, faculty members, and staff came to protest a furlough program that has cut their number of workdays and decreased workers’ salaries by somewhere between 5 and 10 percent for the year, depending on their position and original salary. Programs like History of Consciousness, Language Studies, and Latin American and Latino Studies could soon face serious cuts.

One of numerous protests occurring simultaneously across the Golden State, the UCSC event was a colorful expression of student opinion and demands. There was guerilla theater and slam poetry. Some brought their guitars. They arrived sporting signs with sayings like “Who’s gonna teach, when teachers are on the streets?” By 7 a.m. activists had blocked all entrances to the campus, and UCSC Public Affairs had advised all employees not to come in for work. The protests had effectively shut down campus.

For those in attendance, increasing budget cuts had become a personal matter. Good Times caught up with a handful of those affected to hear their stories.

news1-3Keeping the Books

Ken Lyons, reference librarian for the school’s McHenry Library, also spoke at the rally. He has been affected by the university’s furlough program and is subsequently taking one extra day off a month. But for Lyons, furloughs are the easy part. “That’s the part where I don’t come into work,” says the nine-year faculty member with laugh. “It's the pay cut. That's the big part.”

Lyons, who drives a 32-year-old car he says is “falling apart,” notes that when you take inflation into account, most librarians' salaries are approximately back to what they were in 1999. “And the cost of living has skyrocketed in the past 11 years—certainly around these parts,” he says. “So yeah, it means a lot to me.”

For the 2009-2010 school year, the library has been grappling with a 14.5 percent budget that has forced them to cut back on their services and hours. In spring 2008 the library was open for about 100 hours a week. This year, it's open 67 hours a week. The reduction in hours has forced the library to close one day a week, on Saturdays, a change Lyons calls “appalling for a research university.”

He notices more and more students have been coming to the reference desk looking for a book that isn’t on the shelf but also isn’t listed as “checked out.” “It's because there are just feet after feet after feet of books that need to be re-shelved with nobody to re-shelve them,” Lyons says.

Lyons understands that the university has been tasked with a target budget reduction goal by the state (as part of the governors attempt to fix California’s $20 billion deficit), but he says the cuts are happening in the wrong places. “When you think about it from a corporate perspective, it makes total sense what they're doing,” says Lyons, quickly adding, “but it's wrong.”

Student Government Takes Action

UCSC student Victor Sanchez is the President of the University of California Student Association (UCSA) and the External Vice Chair for the Student Union Assembly (SUA), both of which are trying to protect funding for UC students.

The SUA at UCSC passed a resolution in support of the action, and Sanchez stood in full support of any nonviolent action taking place. “I'll be yelling my lungs out,” Sanchez said before the strike. “Ultimately, being a part of this larger movement is empowering in itself.”

The UCSA has a five-step platform they are promoting this month. It includes full funding for the UC back to 2001 levels and that the legislature looks for alternative revenue sources. But Sanchez says their number one issue is protecting the Cal Grant, a form of student aid for California residents that could soon find itself on the chopping block.

In Sanchez’s first year at UCSC, he lost about four friends who weren't quite able to pay or qualify for the Cal Grant. Sanchez, a Latino/Chicano student, believes the aid is a tremendous asset for underrepresented communities. The Latino student population is currently at 4.7 percent of the total student body, and the African American population is currently 2.6 percent.

Sanchez qualified for financial support, himself, his first year of college. He will be receiving it again for the 2010-2011 school year. The grant pays up $9,700 in student fees depending on the price of the college and the student’s need. The amount of aid varies from one student to another.

Sanchez worries he will still graduate with $20,000 in debt and has been forced to take out loans in order to cover the cost of his education. “God forbid if I want to buy a house by the time I'm 35,” Sanchez says.

Speaking the Language

“I want to remain optimistic,” says language teacher Centineo, adding that it isn't always easy.

The Division of Humanities, which includes UCSC’s language programs, is currently wondering if it will have to cut whole languages in order to make ends meet. One recent proposal includes plans to cut Hindi/Urdu, Portuguese and Russian, a move that would save the division $182,000 per year. This past year, the division already cut 11 percent of Italian classes, the language that Centineo teaches.

“I can't even think about it,” Centineo says. “This is how concerned I am: I can't think about it because I invested all of my resources in this job.”

Centineo is also concerned for her students. She has seen many struggle to keep up in classes as they start working more, sometimes as much as 30 hours a week. Others have been proud to be the first in their families to attend college. They now worry the rising cost of fees might make them the last.

Centineo calls the issue of funding for public education “very personal” because where she comes from in Italy, public higher education for a low price is a higher priority.

“Over there, it's part of our culture that education has to be accessible to all,” she told GT moments after her rousing speech to the crowd, her voice then disappearing into the surrounding chants of “Sí, se puede! Sí, se puede! Sí, se puede!”

The Conversation Continues

news1-2Community Studies Lecturer and Santa Cruz Mayor Mike Rotkin, who will no longer have his teaching job by the end of this school year, believes the University of California is experiencing a “crisis of priorities.” Similarly, Dining Hall workers say that they have faced cuts in pay, while simultaneously being asked to take on more duties like janitorial services.

Participants discussed solutions, such as Assembly Bill 656, which would place a tax on oil companies, repealing Proposition 13, and spending less money on the state’s prison system. But one thing was clear for many of the rally’s attendants: leaving is just not an option.

“For all its faults, I do really love this campus and the students here and my co-workers,” reference librarian Lyons says. “I like the place, and I like who I work with and for, but I don't like the structure.”

Photos by Melissa R. Black

Comments (1)Add Comment
Hey! You voted for them!
written by Steve Hartman, March 10, 2010
80-95% of all UCSC students vote the same way, for the same candidates and the same issues. And just like the California Supreme Court attested to, those candidates and issues are contrary to the wants and needs of the local community.

In Santa Cruz's specific case, it takes over 70% of the local community to vote against your power to keep you from winning every election candidate and/or issue. And you wonder why we don't care if you're hurting? With most normal communities, candidates and issues are decided within the 60-40 margin. So for locals to get a 70% vote against your power is sort of like demanding lower tuition. It's a pipe dream!

To be fair, it's not just you at UCSC. It is "you" UC system wide.

You nearly all vote democrat and the more left the better, just like your lecturers and professors. So if you're looking for sympathy from average middle America, you aren't going to get it. YOU elected these screwballs and now you're suffering some consequences for your actions. Consequences? It's about time, I might add. (By that I mean the actions of the perennial student vote-not your specific vote, per se)

Case in point: The prison union has bought and paid for your democratic leaders in Sacramento. And as you all know, the prisons now get way more money for their budget than the entire state gets for education. Catch my drift? You've voted to make prisons and prisoners a bigger and more valued priority than to yourselves and education.

Start thinking for yourselves, or ask your "local" neighbors how they feel about these situations before you cast your for the pc or academia espoused candidate, and you may one day find salvation. Tuition salvation that is...

Write comment
smaller | bigger

Share this on your social networks

Bookmark and Share

Share this

Bookmark and Share

Hope Amidst Ruin

The Three Levels of Pisces

Sugar: The New Tobacco?

'Girls' On Top

Sign up for Tomorrow's Good Times Today
Upcoming arts & events

RSS Feed Burner

 Subscribe in a reader

Latest Comments

Still Good Luck

Which international current event are you most concerned about lately?

Best of Santa Cruz County

Sante Arcangeli Family Wines


text:
Realm Status
Driven by Distraction is recruiting adults, level 85, who are searching for a guild that has a strong idea of who they are as a team and where they are going.

Please read the public forums before applying to be sure what we are striving for is where you want to be.

We are presently in need of strong healers and a couple adept dps who are quick on the CC.
Others dependent on quality of fit.
Screen Shots
Allied Guilds
Welcome to Driven By Distraction

Driven By Distraction is a guild centered around fairness, teamwork and community. We offer the freedom to do what you want within the game, whether it be raiding with your guild mates, participating in the BG, or sitting around guild chat with a fifth of Cuergo’s Gold, without ever feeling ostracized.

As such we offer a casual self-reliant environment within which to level as well as a more formalized raiding aspect. In this sense, we are a guild within a guild, with different guidelines as such.

As a member of Driven by Distraction you will have the possibility to partake in multiple aspects of the game but never leaving the glowy green chat of friends, which is often one of the most enjoyable aspects of guild membership. We set enough structure in place to provide a holding ground that gives membership the security that they are being led, but not so much that it is officer driven
Other Guild News

The lich king is dead

Luecifer666, Apr 3, 10 10:13 AM.

Fester Down

elderkilmage, Jan 28, 10 1:28 AM.

Rotface down!!!

elderkilmage, Jan 28, 10 1:28 AM.

Saurfang DOWN!!! 25man

elderkilmage, Jan 5, 10 1:38 AM.
Click image for full size...

Heyyyyyyy DbD......

Djynn, Dec 25, 09 11:28 AM.

Who's Online
There are   members online.
25 Man Raid Progression
Speak Up
No shouts have been added yet.

So-and-so has logged on!


text:
Photo detail

Staff Photo: Jason Braverman Atlanta Falcon's Tony Gonzalez fights for extra yards after a reception in the game against the Carolina Panthers on Sunday.

Stories this photo appears in:

Tease photo

Humble Gonzalez closes in on NFL history

Falcon tight end nearing the No. 2 spot on NFL career catches list

Sign in to comment


text:
PA President Abbas with the Jordanian Prime Minister Fayez Al Tarawneh.
Palestinian President Mahmoud Abbas, right, shake hands with Jordanian Prime Minister Fayez Al Tarawneh during their meeting in the West Bank city of Ramallah, October 4, 2012. Photo by AP
Text size

The Palestinian president appears to be backing away from his longstanding demand for Israel to halt West Bank settlement construction before peace talks resume.

Peace talks have been frozen for nearly four years, in large part because of Palestinian demand for a settlement freeze and Israel's refusal to accept it.

While UN recognition is largely symbolic, the Palestinians believe it will bolster them in future negotiations


text:
Happy New Year!

Fun facts to usher in the new year

Hallmark staff
New year's facts

New Year's Day is the oldest and most universal holiday. Throughout early history, cycles of planting and harvesting provided a primitive way to keep track of years. For many cultures, the new year was celebrated in March on the vernal equinox when the sun crosses the equator in the spring and when night and day are of roughly equal length everywhere.

The Romans were the first to observe Jan. 1 as New Year's Day in 153 B.C., according to Hallmark research. Julius Caesar developed the Julian calendar in 45 B.C., retaining Jan. 1 as the beginning of the new year. In 1582, Pope Gregory XIII instituted the Gregorian calendar still in use today, keeping Jan. 1 as New Year's Day.

Did you know?

  • New Year’s Eve is always celebrated December 31; New Year’s Day is always January 1.
  • New Year’s Eve is the largest one-day party event of the year.
  • Because the earth is divided into time zones, the first partiers to usher in the new year are just west of the International Date Line in the middle of the Pacific Ocean.
  • “Auld Lang Syne” is the traditional song sung at the stroke of midnight on Jan. 1. The song, which translates as “old long since” or, roughly, “the good old days,” was written by Scottish poet and lyricist Robert Burns in 1788.
  • Hallmark first made New Year’s cards in 1915.

Ideas' Articles

Select Section

You might also be interested in…


text:
View Single Post
  #11 (permalink)
Old June 30, 2009, 05:37 AM
Sodium Bromate's Avatar
Sodium Bromate Sodium Bromate is offline
Join Date: Jun 2009
Location: Toronto, Ontario
Posts: 33

Originally Posted by Realityshift View Post
Those thermaltake fans IMHO are over rated, Noctuas will easilly be quieter then a thermaltake fan, I agree with the comments made on the build, you did a great job on your original build. I personally like the xigmatek thors hammer HSF over the noctua, I know lots of people will fight tooth and nail for noctua but their HSFs are a tad lacking imo especially for their reletive price point.

The ATCS is a great case and I wish I could afford one, theres no way Id change it out for a haf, although the haf is a decent case, aluminum all the way. Even being a newbie you should look at maybe some prebuilt watercooling kits, just for the fun of it and lowering your temps a touch, I know alot of people call the swiftech kits boring but they always have everything you need and cool decently, and are super easy to setup for a first timer. But really solid first build even if you keep the thermal take fans youll love that computer and it will handle anything you throw at it =)
Thanks for the advice :)
However, my question still stands.
How are the Noctua fans better than the Thermaltake?
They run at the same RPM, yet the Thermaltakes are 3.8 dba quieter.
ISGC vs NF-P12

Again, thanks for the feedback!
Reply With Quote


text:
View Single Post
  #4 (permalink)
Old December 10, 2010, 03:33 PM
SugarJ's Avatar
SugarJ SugarJ is offline
Join Date: Jan 2008
Location: Langley, BC
Posts: 6,000

My System Specs

BitFenix Survivor Review |

BitFenix's Survivor enclosure - The Tech Report - Page 1

BitFenix Survivor

I do really like the look of it. I'd like to do a build in one to try it out, but not for myself.
Reply With Quote


text:
Quantcast The X-Files: Antibodies by Kevin J. Anderson
About The Book
| | More

The X-Files: Antibodies

 On Sale: 10/14/2008
 Formats:     eBook
Adobe eBook Reader
Check Availability
See More

Book Description

When a disease-ravaged body is found in the smoldering ruins of the federally funded DyMar genetic research lab, Agents Fox Mulder and Dana Scully fear that a deadly, man-made plague is on the loose. As the FBI agents investigating the "X-Files" -- cases the bureau has deemed unsolvable -- Mulder and Scully pursue the truth wherever it leads, even into the labyrinthine corridors of the FBI... and beyond.

But when a second corpse turns up, savagely mutilated from within, it's anything but theoretical. Could machines created to cure have learned to kill? Scrambling for answers, Mulder and Scully are opposed at every step by faceless enemies with all the resources of the government -- even perhaps of their own agency -- at their command. Enemies who will stop at nothing to ensure that the secret of immortality falls in the right hands -- their hands.

As sinister forces close in, Scully fights to save the life of an innocent boy while Mulder comes face to face with a crazed and desperate man. A man whose slightest touch brings agonizing death -- and perhaps a resurrection more horrible still.

Author Extras

Books by Kevin J. Anderson
Last Days of Krypton, The Last Days of Krypton, The
The X-Files: Ruins The X-Files: Ruins

New Books Similar to this one
Downton Abbey Script Book Season 2 Downton Abbey Script Book Season 2
View more new releases »


text:
Report a Review

Review:lizmusic45 says:
I like this chapter a lot, and no matter what I always believe in Albus to make the right choices, I just always do that with every story. The thing is, while still believing in him, I loved, loved, loved Minerva so much more.

I love the chess reference at the end to me that was brilliant.

I always thought since day one of reading your stories that you were such a brilliant writer, and hey maybe one day I can write like her, but I never did just because your style is so perfectly wonderful that I couldn't take that, I'd screw it up, besides it belonged with you.

and you know what? it fits you perfectly.

Author's Response: Hey Liz, thank you so much for your review. Albus is a wise man, isn't he? But I am glad you sympathized with Minerva. I've certainly grown fond of her as I write these short stories.

Haha, I am glad you liked the chess reference. It was intentional, I assure you. :)

Thank you for your sweet words. You're a great writer yourself and you've definitely found your own voice. Be unique. I don't think I'm certainly anything to look up to, but I'm unbelievably grateful for your admiration.

Thank you. :)

Your Name:
Reason for this Report:

  • The review is offensive.
  • The review was double posted.
  • The review has formatting problems.
Repeat the number: 839
Submit Report: