West Virginia Water Science Center
This report is available online in pdf format: USGS SIR 2007-5066 (7.8 MB) ()
Mark D. Kozar, David J. Weary, Katherine S. Paybins, and Herbert A. Pierce
U.S. Geological Survey Scientific Investigations Report 2007-5066, 72 pages (Published 2007)
The Leetown Science Center is a research facility operated by the U.S. Geological Survey that occupies approximately 455-acres near Kearneysville, Jefferson County, West Virginia. Aquatic and fish research conducted at the Center requires adequate supplies of high-quality, cold ground water. Three large springs and three production wells currently (in 2006) supply water to the Center. The recent construction of a second research facility (National Center for Cool and Cold Water Aquaculture) operated by the U.S. Department of Agriculture and co-located on Center property has placed additional demands on available water resources in the area. A three-dimensional steady-state finite-difference ground-water flow model was developed to simulate ground-water flow in the Leetown area and was used to assess the availability of ground water to sustain current and anticipated future demands. The model also was developed to test a conceptual model of ground-water flow in the complex karst aquifer system in the Leetown area. Due to the complexity of the karst aquifer system, a multidisciplinary research study was required to define the hydrogeologic setting. Geologic mapping, surface- and borehole-geophysical surveys, stream base-flow surveys, and aquifer tests were conducted to provide the hydrogeologic data necessary to develop and calibrate the model. It would not have been possible to develop a numerical model of the study area without the intensive data collection and methods developments components of the larger, more comprehensive hydrogeologic investigation.
Results of geologic mapping and surface-geophysical surveys verified the presence of several prominent thrust faults and identified additional faults and other complex geologic structures (including overturned anticlines and synclines) in the area. These geologic structures are known to control ground-water flow in the region. Results of this study indicate that cross-strike faults and fracture zones are major avenues of ground-water flow. Prior to this investigation, the conceptual model of ground-water flow for the region focused primarily on bedding planes and strike-parallel faults and joints as controls on ground-water flow but did not recognize the importance of cross-strike faults and fracture zones that allow ground water to flow downgradient across or through less permeable geologic formations.
Results of the ground-water flow simulation indicate that current operations at the Center do not substantially affect either streamflow (less than a 5-percent reduction in annual streamflow) or ground-water levels in the Leetown area under normal climatic conditions but potentially could have greater effects on streamflow during long-term drought (reduction in streamflow of approximately 14 percent). On the basis of simulation results, ground-water withdrawals based on the anticipated need for an additional 150 to 200 gal/min (gallons per minute) of water at the Center also would not seriously affect streamflow (less than 8 to 9 percent reduction in streamflow) or ground-water levels in the area during normal climatic conditions. During drought conditions, however, the effects of current ground-water withdrawals and anticipated additional withdrawals of 150 to 200 gal/min to augment existing supplies result in moderate to substantial declines in water levels of 0.5-1.2 feet (ft) in the vicinity of the Center’s springs and production wells. Streamflow was predicted to be reduced locally by approximately 21 percent. Such withdrawals during a drought or prolonged period of below normal ground-water levels would result in substantial declines in the flow of the Center’s springs and likely would not be sustainable for more than a few months. The drought simulated in this model was roughly equivalent to the more than 1-year drought that affected the region from November 1998 through February 2000. The potential reduction in streamflow is a result of capture of ground water that would otherwise have been discharged to Hopewell Run or its tributaries as base-flow discharge. In addition, because evaporation is the only potential consumptive use of water by the Center, most of the water used is returned to Hopewell Run shortly after use, and the net effect on streamflow downstream of the facility is minimal.
Withdrawal of water from two hypothetical production wells used to represent housing subdivisions of approximately 300 and 500 homes each was simulated to assess the effect of possible suburban development on water availability in the Leetown area. For slightly above normal rainfall conditions, simulated withdrawals form the two production wells did not result in substantial drawdown in the vicinity of the Center’s springs and well fields. An additional reduction of streamflow of 2.3 percent was predicted during slightly above normal hydrologic conditions. For a simulated drought, the hypothetical withdrawals resulted in an additional 5.9 percent capture of surface water, and an additional drawdown of 0.3-1.0 ft near Balch spring and 0.5-1.0 ft near Gray Spring. Actual long-term effects on ground-water levels and streamflow most likely would be less than that simulated because the ground-water flow model did not account for sewage-plant or septic-system return flows to streams or ground water in the area. Because the model simulates long-term average conditions (steady state), effects of short-term hydrologic conditions could be greater than those discussed in this report.
History: First published May 21, 2007
Revised November 13, 2007, to add well numbers missing from Figure 1 and Appendix 3.
This report is available online
in pdf format (7.8 MB): USGS SIR2007-5066 ()
To view the PDF document, you need the Adobe Acrobat® Reader installed on your computer. (A free copy of the Acrobat® Reader may be downloaded from Adobe Systems Incorporated.)
West Virginia Water-Resources Information
For more information, please contact email@example.com.