How to Interpret DCS and PLC Symbols on a P&IDLearn about how to correctly interpret PLC and DCS symbols on a P&ID.
Alright then…let’s get started.
A P&ID is a road map
Anybody such as Instrumentation & Control engineers, technicians, and maintenance personnel working on industrial plant control systems depend heavily on P&ID’s.
A P&ID is like a road map telling us what the instruments and devices are, where they are located, and how they interact with the rest of the plant.
Original P&ID symbols
Original symbols and terminology for P&ID’s were created long before the introduction of PLC’s and DCS’s in plant control.
Old industrial processes and control rooms
Before computers came along, process control loops were stand-alone. In other words, each process had its own individual controller.
Control rooms were massive and had sprawling control panels with lots of controllers and other devices such as strip chart recorders and switches.
New industrial processes and control rooms
Today’s industrial processes are controlled by computerized systems using virtual controllers found in PLC’s and DCS’s.
New control rooms are filled with HMI’s and keyboards connected to a DCS or a PLC system. All of this computerization required that new P&ID symbols had to be developed.
P&ID symbols for PLC and DCS
P&ID symbols for DCS
So, let’s look at the P&ID symbols for PLC and DCS. If you recall, stand-alone instruments are indicated on a P&ID by a circle with a tag number.
The horizontal bar across the middle of the circle indicates the physical instrument resides in a primary location accessible to an operator on the main control panel.
If we take that same symbol and draw a box around it, it now means that it is no longer a physical instrument. It is now part of a shared display and shared control in a DCS.
P&ID symbols for DCS on HMI
Ok…Let’s look at a P&ID with DCS symbols and see how it links field instruments with the DCS and how it’s displayed on the Operator HMI.
LT501 and FT501 are 2 field instruments both sending electrical signals to DCS controllers.
P&ID symbols for DCS on Flow Control Loop
Let’s take a closer look at the Flow Control Loop. Flow Transmitter FT501 sends an electrical signal to the DCS Flow Indicating Controller FIC 501, which in turn sends an electrical signal to operated Flow Control Valve FCV501.
Here’s what the Operator sees on the HMI screen…We’ve put a big red circle around FIC501 and FCV501.
As we discovered on the P&ID, the controller FIC501 is part of the DCS. FIC501 controller functions can be adjusted at the HMI by the Operator.
All FIC501 inputs and outputs can be observed in real-time on the HMI as well.
Ok…Let’s drill down a bit deeper and look at how the P&ID relates to the Flow Loop Diagram. We’ve placed green circles around FT501 and FIC501.
Referring back to the P&ID, you will see that FT501 is a Flow Transmitter in the field, and FIC501 is a shared control in the DCS.
This is a good time to point out the blue circle around the Software Signal lines as they show how the DCS connects with the HMI.
P&ID symbols for PLC
PLC symbols don’t show up on P&ID’s nearly as often as DCS symbols. But, when they do show up, they are drawn as a diamond inside a box.
All you have to know is that the symbol represents a software instruction to perform some function in the plant.
For example, let’s revisit our P&ID. The PLC symbol indicates that the SDV503 valve is operated by the Emergency Shutdown software instruction written in the PLC program.
Let’s review what we’ve discussed today:
– DCS and PLC symbols became a necessity with the computerization of process automation.
– If you see a square box drawn around the circle on a P&ID, that means a DCS is part of the control process.
– If you see a square with a diamond in it on a P&ID, that means a PLC is part of the control process.
Want to Learn More?
Newcomers to RealPars have free access to one of our online courses.
You can take advantage of this offer by downloading the RealPars app (iOS, Apple TV, Android, Android TV, FireTV, Roku) and selecting the first lesson of the PLC Hardware course. Just like the video, the lessons are all high-quality and also very easy-to-follow.
Also, for a low monthly fee, you’ll get full access to an exclusive library of courses on PLC programming and industrial automation topics as well as new fresh out of the oven videos each and every week. These courses are all member-exclusive and are not shared anywhere else on the internet.
If you would like to get additional training on a similar subject please let us know in the comment section.
Check back with us soon for more automation control topics.
Got a friend, client, or colleague who could use some of this information? Please share this article.
In this blog post, you’ll learn about the mindset that helped me getting a PLC programming job with NO experience. This is my personal experience as someone who searched for a job in this field and as an employer who reviews resumes and interviews candidates for a variety of projects. So let’s get started!
So how does a diode module or diode block work? For you to be able to understand how a diode module works, you first need to understand how a single diode actually works.What is a diode? A diode is a device that allows current to flow in only one direction. That...
So, what is a floating license and how is it different from a standard software license? In short, a standard software license is for exclusive use whereas a floating license is for shared use.You buy a floating software license when you want to share the use of...
Learn how to program PLCs, install and wire industrial devices, and at the same time purchase them online.
+31 10 316 6400
Mon - Fri 8:30 am to 5:30 pm (CET)
Rotterdam Science Tower, Marconistraat 16,
3029AK Rotterdam, Netherlands
© 2020 RealPars B.V. All rights reserved.
Created with coffee and tea in Rotterdam.