Yan Evans, vice president of the UK Sales Unit at Fläkt Woods, explains more.
The Carbon Trust has stated that air conditioning can increase a building’s energy costs and associated carbon emissions by up to 100 per cent, and it is estimated that cooling consumes up to 14 per cent of UK electricity. As the EU has set a target for a 20 per cent reduction in energy consumption by 2020, the focus on air conditioning efficiency is likely to increase.
No Noise, Less Expense
Chilled beams circulate air using the principles of natural heat convection and their major advantage over more common forced-air systems is that they circulate air without the noise and expense of ductwork and air handlers. Typically mounted overhead, the beam is chilled by an external source such as recirculated water and cools the space below by acting as a heat sink for the naturally rising warm air of the space.
Water temperatures in chilled beams are higher than in fan coil systems – typically 14°C flow compared to 6°C – which enables the chiller to perform more efficiently. Chiller energy savings for a chilled beam system compared to an FCU can be as much as 35 per cent.
More Chilled Beam Benefits
FCUs also normally need a filter to prevent the coil becoming clogged with dirt caused by the coil becoming wet. In contrast, a chilled beam system needs no condensation protection because the chilled water temperature is typically above a room’s dew point and, as the chilled beam coil is dry, there is no need for a filter.
As well as considering the impact on energy costs of air conditioning systems, specifiers and building owners often need to consider future-proofing. In many building projects – particularly office and retail spaces – the HVAC systems are designed and installed without knowledge of how the space is likely to be divided in the future, so flexibility can be a key consideration.
Where there is the likelihood that a building will be re-structured internally during the lifespan of its systems, with walls, occupancy levels and room functions changing, HVAC systems need to be flexible.
More Flexible Than You Might Believe
With Wega II, floor layouts can be changed without the need for moving or installing new beams, requiring only simple adjustment and reconfiguration of the FPC vanes and the variable position nozzles. Equally the Pi functionality, being pressure independent and making the Wega II suitable for many types of ductwork, is designed for change.
It can be easily moved by disconnecting, reconnecting and resetting the values. The design also includes variable geometry nozzles, which offer an optimum choice of airflow settings. Nozzle change can be actuated to adjust ventilation flow rates automatically to occupancy levels, regardless of pressure changes in the ductwork system.
What's the Demand for Chilled Beams?
And, as new generations of chilled beam systems come to market, their ease of installation, potential for energy saving and long term flexibility represent an increasingly attractive alternative to FCUs for the specifier, designer and end user alike.